What type should I use in WinCC Flexible to set time to a PLC variable of type S5TIME ? I have tried INT but is does not work.
Hello Per Olof,
It is also possible to do it simply in PLC side.An integer
in HMI transferred to "MW 10",this value (number of seconds)
converted to DINT,multiplied by "1000" to be interpreted as
data type "time".Finally using FC40 "TIM_S5TI" to convert it
to S5 Timer.Note limitation of "9990s" as S5T#2h46m30s.
|=== Edited by hdhosseini @ 5/30/2012 5:34 PM [GMT ] ===|
Human beings are members of a whole , In creation of one essence and soul